91A SPEC 191 Rev May 1995
THE FOLLOWING DATA IS INTENDED TO ASSIST IN SPECIFYING PEMKO
PRODUCTS. INCORPORATE IN A PROJECT SPECIFICATION WHERE
CAREFULLY REVIEW TO ENSURE COORDINATION WITH ALL CONTRACT DOCUMENTS.
1. PRODUCT: Floor Plate (1/4" X 3"), Pemko #191A
PEMKO * Ventura PEMKO * Memphis
4226 Transport Street 5535 Distribution Drive
Ventura, CA 93003 Memphis, TN 38141
Phone:(800) 283-9988 Phone (800) 824-3018
Fax: (800) 283-4050 Fax: (800) 243-3656
3. MATERIAL & FINISH:
PRODUCT SELECTED IS AVAILABLE IN MATERIALS & FINISHES SPECIFIED
BELOW. WHERE MORE THAN ONE MATERIAL IS LISTED FOR A PRODUCT,
SELECT PARAGRAPH FOR MATERIAL YOU WANT.
EDIT BRACKETED TEXT TO SPECIFY FINISH. DELETE TEXT NOT DESIRED.
MATERIALS & FINISHES NOT LISTED MAY BE AVAILABLE BY SPECIAL
* Alloy Type 6063-T5
* Chemical and physical properties per the Aluminum
* Federal Specification QQ-A-200/9C
* [191A Mill finish, 191D Dark bronze anodized,
191G Gold anodized].
Architectural bronze (brass), Extruded
* Note: Brass is fluted both sides.
* CDA alloy 38500 (56.5% Copper, 2.75% Lead, 40.7% Zinc,
* [191B Mill finish, Oxidized & oil rubbed, Polished, Satin
4. TEST & CODE COMPLIANCE
Handicapped: Complies with CABO/ANSI A117.1-1992, ADA 1990;
and ADAAG 1991 guidelines.
Fire Label: Classified By UL For Application To Swinging
Type Fire Doors of the Hollow Metal or Steel
Covered composite type Rated up to 3 Hours, or
Wood Core Fire Doors rated up to 1-1/2 Hours.
Listed and Labeled as Gasketing Materials.
Tested in accordance with UL10B by Underwriters
Laboratory, Inc. .
Smoke Label: Labeled as Gasketing for Smoke Control Doors.
Tested per NFPA 105 by Wyle Laboratories.
Installation to be performed in strict accordance with
manufacturer's instructions furnished with product.
Carefully cope to fit within the frame opening. Fasten with
flat head wood or machine screws provided and appropriate
anchors as required. Use a sealant or compound at all edges
Guaranteed by manufacturer against defects in material or
workmanship for 3 years.